Simulation Study on Ventilation System of the Equipment Room for CCHP System
Abstract: Heat dissipation between equipments of CCHP system, which need well organized ventilation to assure the optimum temperature for equipments running. It costs much to obtain the ventilation plan by experimental method; it is necessary to use simulation as an auxiliary for the design of ventilation system. By the building of mathematical model of equipments and using the software Fluent for numerical analysis of the temperature field between equipments, this paper gives the improvement scheme for air distribution mode and design criteria for ventilation. According to the improved ventilation system, the extra use of cold wind equipment can decrease the running temperature of power generator effectively by simulation under the condition that the inlet air temperature is equal to the design temperature 307 K of outside in summer. In winter, when the inlet air temperature is equal to the design temperature 269.4 K of outside, the use of natural air inlet and forced air exhaust can keep the running ambient temperature between equipments, which can save operation costs of the system.
文章引用: 许伟明 , 王瑞祥 , 许家琪 (2015) 燃气冷热电三联供的设备间通风系统模拟研究。 可持续能源， 5， 49-59. doi: 10.12677/SE.2015.55007
 张巧慧 (2006) 电厂汽轮机房通风和采暖的CFD模拟与节能策略研究. 硕士论文, 浙江大学, 杭州.
 赵彬, 李先庭, 彦启森 (2001) 用零方程湍流模型模拟通风空调室内的空气流动. 清华大学学报(自然科学版), 10, 109-113.
 谷现良, 赵加宁, 高军, 高甫生 (2003) CFD商业软件与制冷空调. 制冷学报, 4, 45-49.
 万鑫, 苏亚欣, 杨艳超 (2008) 工业厂房自然通风的数值模拟及结构改进. 中国安全科学学报, 8, 103-108
 Abanto, J., et al. (2004) Airflow modelling in a computer room. Building and Environment, 39, 1393-1402.
 Cheong, K.W.D., et al. (2003) Thermal comfort study of an air-conditioned lecture theatre in the tropics. Building and Environment, 38, 63-73.
 赵彬, 李先庭, 彦启森 (2000) 用CFD方法改进室内非等温送风气流组织设计. 应用基础与工程科学学报, 4, 376-386.
 黄雪莲, 戴有为, 梅启元 (2003) 空调房间气流组织的数值模拟. 南京理工大学学报(自然科学版), 4, 41-44.
 赵琴, 王倩 (2003) Fluent在暖通空调领域中的应用. 制冷与空调, 1, 15-18.
Cho, H., Mago, P.J., Luck, R. and Chamra, L.M. (2009) Evalution of CCHP systems performance based on operational cost, primary energy consumption, and carbon dioxide emission by utilizing an optimal operation scheme. Applied Energy, 86, 2540-49.
Kong, X.Q., Wang, R.Z. and Huang, X.H. (2004) Energy efficiency and economic feasibility of CCHP driven by stirling engine. Energy Conversion and Management, 45, 1433-42.
Mago, P.J. and Chamra, L.M. (2009) Analysis and optimization of CCHP systems based on energy, economical, and environmental considerations. Energy and Buildings, 41, 1099-1106.
Fumo, N. and Chamra, L.M. (2010) Analysis of combined cooling, heating, and power systems based on source primary energy consumption. Applied Energy, 87, 2023-30.
 Cho, H., Eksioglu, S., Luck, R. and Chamra, L.M. (2008) Operation of micro-CHP system using an optimal energy dispatch algorithm. ASME Proceedings of Energy Sustainability, Jacksonville, 10-14 August 2008.
 Mago, P.J., et al. (2010) Analysis and optimization of the use of CHP-ORC systems for small commercial buildings. Energy and Buildings, 42, 1491-1498.
 朱铮, 杨其才, 刘刚, 冯震 (2011) 电厂自然通风方式的选择. 制冷与空调, 2, 138-141.
Kindangen, J. (1997) Effects of roof shapes on wind-induced airmotion inside buildings. Building and Environment, 32, 1-11.
Haves, P., Linden, P.F. and Graca, G.C. (2004) Use of simulation in thedesign of a large, naturallyentilated office building. Building Services Engineers Research and Technology, 25, 211-221.