Cause Analysis and Measures of the Camera Struck Repeatedly by Lightning in Security Monitoring System
Abstract: This paper analyzes the lightning data of the security monitoring system in the scope of lightning site. The results show that the frequency of thunderstroke in the two years is up to 17 times at the range of 500 meters. Among them, there is only 1 time that the rolling sphere radius of lightning current is larger than the average distance from the lightning point. There are 15 times that lightning impulse electromagnetic induction intensity in LPZ0B area is not less than 0.07 × 10−4 T, which is 88.2% of the total amount, and there are 6 times that lightning impulse electromagnetic induction intensity in LPZ1 area is not less than 0.07 × 10−4 T, which accounts for 35.3% of the total amount. From the results, it is proved that the indoor and outdoor cameras are unlikely to suffer direct lightning flash strike, and in most cases cameras are subjected to inductive lightning, which is the main reason of the camera repeatedly struck by lightning. Therefore, the study has some guidance to the lightning protection of the security camera monitoring system.
文章引用: 骆明佐 , 邓 逸 , 吴小红 , 许根源 , 石 磊 , 孙 川 (2014) 安防监控系统摄像头屡遭雷击原因分析与措施。 安防技术， 2， 26-36. doi: 10.12677/JSST.2014.23005
 四川省住房和城乡建设厅 (2012) GB50343-2012建筑物电子信息系统防雷技术规范. 中国建筑工业出版社, 北京, 7.
 李伟, 董晓红, 骆明佐 (2012) 一个典型的雷电散击案例调查及应对措施. 高原山地气象研究, 2, 81-82.
 中国机械工业联合会 (2011) GB50057-2010建筑物防雷设计规范. 中国计划出版社, 北京, 46-49.
 骆明佐 (2011) 石油管理站电子设备设施遭雷击分析. 高原山地气象研究, 2, 71-72.
 全国雷电灾害防御行业标准化技术委员会 (2013) QX/T186-2013安全防范系统雷电防护要求及检测技术规范. 中国气象出版社, 北京, 2-3.